Carroll Meynell 5003/3 Transformer Triple Outlet Rating 5kVA Continuous 2.5kVA
(Please note images of products are for representation purposes only. Whilst every care is taken to provide accurate images of products, actual products may differ slightly.)
Carroll & Meynell transformers are primarily for use when using portable electric tools on outdoor sites.
They are manufactured to BS EN 61558 and have thermal overload protection and with BS EN 60309 output sockets as standard. They have a glass reinforced polyester case and input flex and 13 amp plug. The 5kVA model is without a fitted plug, max input current 23 amp.
The Carroll & Meynell transformers are completely encapsulated for extra weatherproofing.
These transformers are rated for intermittent operation at their maximum listed power capability for a duty cycle of 25%. i.e. 5 minutes ON 15 minutes OFF. They may be used in a continuous operation mode at a rating of 50% of their maximum capability. E.g. a 3.3kVA unit may be operated continuously at 1.65kVA.
2 x 16 amp outlets, 1 x 32 amp outlet.
This item shipped without an input plug. Maximum input current 23A.
Portable Tool Transformer - Safety Instructions
1. The transformer will get warm in normal use, make sure that the heat will not damage any floor covering that it is standing on. It is not advisable to place the transformer onto carpet, vinyl floor covering, etc., and use at continuous rating for any length of time.
4. Although the transformer may be of insulated construction, it is not double insulated (class 2) and the earth pin of the output socket must be connected to the centre point of the secondary winding and to the transformer incoming earth.
2. The transformer may be fitted with an over temperature cut-out switch, in the event of this operating, let the unit cool down then reset the cut-out switch before using again.
5. Power tool transformers must not be tested as class 2 appliances on portable appliance testers, flash test only at 1.5kVA.
3. Check the transformer power rating against the power rating of the tool you are going to use. The transformer can supply portable tools in normal use up to the rating shown on the transformer and consultation with the above table. Care should be taken when using the transformer to supply constant loads, i.e. floodlights, wallpaper strippers etc. The transformer can only supply about half of its rated power to continuous load like this.
6. Power tool transformers have an inherent high inrush current, in the event of the fuse blowing on switch, check that the fuse in the input plug is suitably rated and is of the anti-surge type. Miniature circuit breakers protecting the sockets should have a type 4 tripping characteristic.
|Manufacturers Part Number||CM5000/210/PT|
|Ebay Category ID||181938|
|Package Height (cm)||36|
|Package Width (cm)||30|
|Package Length (cm)||36|
|Bullet 1||Manufactured to BS EN61558.|
|Bullet 2||Have thermal overload protection.|
|Bullet 3||BS EN60309 output sockets as standard.|
|Bullet 4||Completely encapsulated for extra weatherproofing.|